Key points of spring vibration isolator construction:
1. Simple product structure, superior function, easy installation, wide range of Shared load.
2. The vibration isolation design components of the pump unit shall be calculated according to the pump model and specification, speed, system quality, installation location, load value, frequency ratio requirements and other factors.The vibration isolation frequency of the pump set should be between 2 and 5 than np.
3. Rubber vibration damping pad is generally used for horizontal water pump, and multi-layer rubber vibration isolation pad or damping spring vibration isolator should be installed on the floor.
4. Rubber vibration isolator should be used for vertical water pump.
5. The supporting points of the vibration isolation components should be even, but not less than 4. The model, specification and function of the vibration isolation components of each supporting point of a water pump set should be consistent.